A confirmation test was done on the three fixtures that showed low levels of lead but enough to do additional testing on. A 30 second flush test was also done on these fixtures which showed that the lead levels dropped to under remediation levels. This indicates that the elevated levels of lead are coming from the fixtures itself. In order to correct this issue two of the kitchen faucets will be changed and the gym drinking fountain will be eliminated. After replacement of these fixtures additional testing will be done to confirm that this issue has been addressed.